for Dover, NJ
On site to replace water motor gong.
Sprinkler Service Call, dry system tripped
On site for priority service call for tripped dry system.
** YOUR PARTS WILL BE READY FOR PICK UP AT FERGUSON IN PASSAIC MID-MORNING ! ORDER 5284342 / 5284354 ** Confirmed appt with Veronica 973-537-0090 on site: see Jimmy tech arrival: 8-9am Fire sprinkler emergency call Costumer call for a leak on the system (someone hit the sprinkler pipe with a forklift) Upon arrival system was found shut off (by others) Leak was coming from a 3x2 1/2x1 1/2 t, took the side that was leaking (2 1/2) and install a 2 1/2 hose valve just to cap the t for now this is a temporary repair. The t seems to be ok and not leaking. we have to come back with a piece of pipe (2 1/2 pipe 23 1/2 long with one side threaded and the other groove). System is back on service, but Part of the building is not protected till repairs are completed. 5)hours 2 tech (costumer has a cage for the forklift but a 12’ ladder will work Tech to groove the existing 2 1/2 pipe Material need it 2 1/2 pipe 23 1/2 long groove one side threaded on the other 1)2 1/2 groove coupling. Alarm did not
Confirmed appt with Claudia #973-292-0170 tech arrival: 8:30-10am Annual sprinkler inspection ** ANOTHER TECH TO BE ON SITE FOR THE EXTINGUSIHERS ** Sprinkler Inspection