Confires Fire Protection
Maritza - Moorestown, NJ
Dinesh Patel - Princeton, NJ
Very prompt and satisfactory service. Excellent
Ashley - Scotch Plains, NJ
Sr Maria - South Plainfield, NJ
1. Confines has been monitored our fire system for years and technician asked me how to turn off the alarm so he can do the test. It seems that the technician did not make aware about this. If no one there to mention that Confires has been monitored our alarm system so that the technician could call the office to confirm, how can the inspection be fully completed? 2. There has been no change in the system since June 2019, and yet now there is a finding that needs to be fixed. The technician said it was mentioned on a report in 2018. However, it was not mentioned at the inspections in July 2019 and Jan 2020. Why? I am very confused.
Dino - Flemington, NJ
Bill came on time was very courteous I asked him to give me a call when he was finished and he did . Problem solved . Thank you
Kyle and Jethro did a great job..
Joe - Clinton Township, NJ
Patricia - South Orange, NJ
Everything went well with the inspection and changing out of the fire extinguishers!
Angela - Maplewood, NJ
Dwayne was fast, efficient and timely and I would definitely recommend Confires services to others and use them again in the future.
Joyce - Newark, NJ
Leonard - Branchburg, NJ
COD ACCOUNT- MUST COLLECT PAYMENT/CUSTOMER IS AWARE- $240.55 WITH TAX Confirmed with Najee #848-248-8028 Email: email@example.com Tech Arrival: 2:45pm - 3:00pm Semi-Annual Inspection (1) Kitchen System Kitchen Suppression Inspection Semi-Annual Inspection Dept: Kitchen Suppression
Confirmed appt with Ran 908-687-5400 tech arrival: 8am 5 year hydro test on the fire department connection was performed. We found the pit full of water we drained the water and perform the test. Pipe is really corroded inside of the pit. Results of 5 year hydro test are unsatisfactory components on the FDC line lost pressure on the 2 hours test. We recommend the pipe after the FDC check valve to be replace; the located is inside of the pit.The elbow after the check valve is extremely corroded. Material needed 5’ of sch40 pipe check the shop for this pipe. 1)4” groove elbow 1)4” flange to groove fitting 1)4” bolts and nuts pack Tech to cut and groove the piece of existing 4” pipe going up to the FDC. Connection. Also tech should bring pump just in case is full of water again. Sprinkler Repair
Sprinkler and Backflow Inspection
Sprinkler Inspection, annual sprinkler inspection
Sprinkler Service Call, repairs and system restoration of unit 21
Sprinkler Service Call, pump running
Providing faster, smarter, and more efficient fire protectionLearn more here